The pull-out disconnects may not disable power to the air handler, posing an electrical shock hazard to individuals servicing the units.
Goodman toll-free at 844-633-4295 from 8 a.m. to 5 p.m. ET Monday through Friday or online at www.goodmanmfg.com and click on “Air Handler Product Recall” at the top of the page for more information.
This recall involves Goodman air handler models AWUF and ACNF (A = Air Handler; W = Wall Mount; C = Ceiling Mount; U = Unpainted; N = Uncased; F = Flowrater). The recalled air handlers are most often installed in apartment and condominium units and are used with heating and cooling systems to provide climate control. The AWUF model units are wall mounted, while ACNF model units are ceiling mounted. The recalled air handlers have serial numbers beginning with 1511, 1512, or 1601 through 1610. The serial number is located on the label found by removing the wall panel (for AWUF units) or ceiling panel (for ACNF units).
Consumers should immediately contact Goodman for a free inspection and free repair. Goodman is contacting all known commercial owners directly.
Goodman has received reports involving six units at two locations of the air handlers remaining powered when the disconnect handles were removed. No injuries have been reported.
Note: Individual Commissioners may have statements related to this topic. Please visit www.cpsc.gov/commissioners to search for statements related to this or other topics.
The U.S. Consumer Product Safety Commission (CPSC) is charged with protecting the public from unreasonable risk of injury or death associated with the use of thousands of types of consumer products. Deaths, injuries, and property damage from consumer product-related incidents cost the nation more than $1 trillion annually. CPSC's work to ensure the safety of consumer products has contributed to a decline in the rate of injuries associated with consumer products over the past 50 years.
Federal law prohibits any person from selling products subject to a Commission ordered recall or a voluntary recall undertaken in consultation with the CPSC.