Recall Details Report an Incident Involving this Product
This recall involves Square D brand models FA, FH, FI and FY one-, two- and three-pole circuit breakers rated 15 to 100 amps, and model KI two- and three-pole circuit breakers rated 110 to 250 amps. The F model breakers were manufactured May 8, 2013 through June 10, 2013 and have date codes 13193 through 13241. The K models were manufactured May 2, 2013 through June 21, 2013 and have date codes 13184 through 13255. The date codes are YYWWD format (example: 13184 = year 2013, week 18, day of the work week 4/ Thursday). The circuit breakers have a yellow label with the words “Square D” or the Square D logo. Model information can be found on the faceplate.
Consumers should immediately check to see if they have the recalled circuit breakers. Consumers with uninstalled products will receive a replacement. Installed products will be replaced at no charge to the customer with an allowance of up to $300 per site to cover labor costs.
Schneider Electric USA Inc., of Palatine, Ill.