This recall is for the ILI-MB-E3 and ILI-S-E3 Gamewell-FCI fire alarm panels in commercial buildings. This issue is limited to a specific configuration of Signaling Line Circuit (SLC) devices. To occur, the SLC must include at least two of the following detectors in any combination: Acclimate, 4-Warn, Photo/CO and iFAAST. The issue would occur only if the detectors are addressed within the same FlashScan polling group. Detectors installed in a different combination are not affected.
Authorized distributors from May 2015 through August 2015 for about $800.