This recall is for the ILI-MB-E3 and ILI-S-E3 Gamewell-FCI fire alarm panels in commercial buildings. This issue is limited to a specific configuration of Signaling Line Circuit (SLC) devices. To occur, the SLC must include at least two of the following detectors in any combination: Acclimate, 4-Warn, Photo/CO and iFAAST. The issue would occur only if the detectors are addressed within the same FlashScan polling group. Detectors installed in a different combination are not affected.
Authorized distributors from May 2015 through August 2015 for about $800.
The U.S. Consumer Product Safety Commission (CPSC) is charged with protecting the public from unreasonable risks of injury or death associated with the use of thousands of types of consumer products. Deaths, injuries, and property damage from consumer product incidents cost the nation more than $1 trillion annually. CPSC’s work to ensure the safety of consumer products has contributed to a decline in the rate of deaths and injuries associated with consumer products over the past 40 years.
Federal law bars any person from selling products subject to a publicly announced voluntary recall by a manufacturer or a mandatory recall ordered by the Commission.
For lifesaving information:
Please use the below phone number for all media requests.
Phone: (301) 504-7908
Spanish: (301) 504-7800