Note: company can not be contacted.
|FOR IMMEDIATE RELEASE
|Originally issued November 12, 1988; Revised January 15, 2004
|Release # 88-095
Challenger Electrical Equipment Corp. Offers Replacement Program For 9000 GFCI Circuit Breakers
WASHINGTON, DC- In cooperation with the U.S. Consumer Product Safety Commission (CPSC), Challenger Electrical Equipment Corp. of Malvern, Pennsylvania, voluntarily offered free replacement of its 15 and 20 ampere type HAGF single pole ground-fault circuit-interrupter (GFCI) circuit breakers.
These type HAGF-15 and type HAGF-20 circuit breakers were manufactured between February 22, 1988 and April 29, 1988, and most were sold nationwide to electrical product distributors during this period. Some may have been sold to consumers by retail hardware or lumber outlets. Approximately 9000 of these devices have not been located, some of which are believed to have been installed in residences.
Type HAGF ground fault circuit breakers are devices, which provide protection to consumers against severe electric shock and electrocution as well as providing the normal circuit breaker functions of interrupting short circuits and electrical overloads.
Although no electric shock incidents have been reported by Challenger, the firm recalled this product because is has determined, by quality control testing, that a mechanical part may become detached and prevent the ground fault feature of the circuit breaker from functioning. (The normal circuit breaker functions are not affected by this problem.)
They protect residential 15 ampere and 20 ampere circuits including receptacle outlets in bathrooms, kitchens, basements, garages and outdoors as required by the National Electrical Code. The code also requires GFCI protection for receptacles in hotel and motel bathrooms. The HAGF circuit breakers, which may require replacement, are located in the electrical service panel. If the name "Challenger" is embossed on the front of the panel (on the door handle) and/or on the label on the back of the panel/door, that panel may contain circuit breakers requiring replacement. Affected circuit breakers have a yellow button and the word "test" in raised letters on one side; on the other side, the number 15 or 20 is printed on the handle in white letters between the raised words "ON" and "OFF."
If the number on the handle is black or if there is a label it with white lettering next to the word "test , then the HAGF circuit breaker will not need to be replaced.
Consumers should note that the HAGF circuit breakers which require replacement will only be found in dwellings which have been constructed since February 1988 or in which electrical work has been done since February 1988.
Consumers who believe that they have installed HAGF circuit breakers requiring replacement should contact a licensed electrician to perform this work. Power to the panel should be shut off before inspecting and removing breakers.) The company is no longer able to be contacted at the phone numbers provided in the original press release.
The Consumer Product Safety Commission believes that GFCI's provide a significant level of electrical safety. The Commission recommends that all GFCI's (whether circuit breaker or receptacle type) be tested frequently, at least monthly, using the test button on each unit.
The U.S. Consumer Product Safety Commission is charged with protecting the public from unreasonable risks of injury or death associated with the use of
thousands of types of consumer products under the agency’s jurisdiction. Deaths, injuries, and property damage from consumer product incidents cost the
nation more than $1 trillion annually. CPSC is committed to protecting consumers and families from products that pose a fire, electrical, chemical or
mechanical hazard. CPSC's work to help ensure the safety of consumer products - such as toys, cribs, power tools, cigarette lighters and household
chemicals -– contributed to a decline in the rate of deaths and injuries associated with consumer products over the past 40 years.
Federal law bars any person from selling products subject to a publicly-announced voluntary recall by a manufacturer or a mandatory recall ordered by the
To report a dangerous product or a product-related injury go online to www.SaferProducts.gov or call CPSC's Hotline at (800) 638-2772 or teletypewriter at
(301) 595-7054 for the hearing impaired. Consumers can obtain news release and recall information at www.cpsc.gov, on Twitter @OnSafety or by subscribing
to CPSC's free e-mail newsletters.